We are a leading Manufacturer of 11 kv compact substation with panel, 2500 kva compact substation and compact substation from Dholpur, India.
11 Kv Compact Substation with panel
Get Best Quote
Approx. Price: Rs 10 Lakh / PieceGet Latest Price
Minimum Order Quantity
Number of Phase
630 kva compect substaion for industry.Focusing on a customer centric approach,Gaurav has a pan-India presence and caters to a huge consumer base throughout the country. Buy Control Panel Boards in bulk from gaurav and quality-assured.
We manufacture distribution transformers upto 5 mva capacity with 11/33kv class. Transformers cores are built with crgo, low loss silicon steel lamination. Use of high grade and laser scribed laminations for the core significantly reduce no load losses and noise levels as committed. Power transformer winding are made of electrolytic grade copper with continuously transposed conductors as per the designs requirement. The winding has axial and radial cooling ducts to ensure effective heat dissipation into the oil and elimination the hot spots. For high voltage windings, disc coil with excellent mechanical strength are used to take the stresses due to voltage level. A special interleaved or shielded construction offers most uniform voltage distribution despite system transients. Power transformers, core-oil assembly are rigidly supported by a common pressure ring of dandified wood at the top and bottom, for precise alignment. Well profiled angled rings are placed between hv and lv windings to reduce voltage stress levels. The ends an tapping leads to all the windings are connected by special extra flexible, insulated copper cables, which are rigidly braced in position. The core-coil assembly is put into the tank with proper location arrangements. The tank is then filled with hot oil, filtrated by high vacuum oil filtration plant. Power transformers, tank are built with mild steel plates to withstand full vacuum. Conforming to the international standards. Lugs for jacking, lifting and hauling are routinely tested for dye penetration. Tanks have welded or bolted top cover. Tanks are shot blasted to get a surface finish to have double coat of epoxy pint after double coat of epoxy primer. The transformer is made read for final inspection after assembly of bushings, conservator, and radiators etc.